The EcoSensors OS-6 Ozone Monitor has a safety control relay built in that is set to activate above the ozone human safety limit of 0.1 ppm. When this relay is wired to the Remote Alarm Panel (RAP-1), a loud audible alarm and flashing light will activate when ozone levels go above 0.1 ppm. This blog explains how to wire the RAP-1 to the safety control relay on the OS-6 Ozone Monitor.
Step 1: Remove the front panel on the OS-6.
Step 2: Insert tip of RAP-1 free cable through one of the nipples on the bottom of the OS-6 monitor.
Step 3: Locate the control relay labeled “ABOVE 0.1 PPM.” Connect the red wire to the Normally Open (N/O) terminal and the black wire to the Common (COM) terminal.
Step 4: Replace the OS-6 front panel.
The OS-6 is now wired to the RAP-1. When mounted on a wall and powered on, an audible and visual alarm will now activate when the ozone levels are above the human safety limit of 0.1 ppm.
Purchase OS-6 Ozone Safety Monitor Here: https://www.oxidationtech.com/os6-ozone-monitor.html
Purchase RAP-1 Remote Alarm Panel Here: https://www.oxidationtech.com/rap-1.html
Watch video showing how to wire OS-6 Ozone Detector to RAP-1: